Supply of # 2 complete horizontal centrifugal pump w/ turbine and base plate
Item: P 403 / P.F. 1 No. of stages: six
Liquid handled: HC liquid (heavy naphtha)
Specification: normal design
Capacity in GPM @ P.T.: 166 179
Suc. Press. P.S.I.G: 0 33
Disch. Press. P.S.I.G: 850 850
Diff. Press. P.S.I: 850 817
Vapor Press @ P.T: NIL 15
Design Head (ft): 2700 2780
N.P.S.H. (avai.) (Ft): FLOODED
N.P.S.H. (reqd.) (Ft): 8
Pumping Temp. (°F): 100 217
Specific Gravity @ P.T.: 0.728 0.679
Viscosity @P.T. (SSU) CPS: 0.57 0.30
Nozzles / Suction: 4" 600 # ASA R.F. (Top)
/ Discharge: 2" 600 # ASA R.F. (Top)
Thrust Bearing: Kingsbury
Radial Bearing: sleeve
Bearing Lubrication: Forced FEED
Pump should be according to API 610 Last Edition, between bearing mounted (API BB5)
Pump should be equipped with:
Mechanical seal exclusively from (John Crane or Burgmann)
Flexible coupling, with spacer.
Non-sparking coupling guard.
Inlet Steam Temp. °F: 480
Inlet Steam Press. PSIG: 210
Inlet Steam Press. (Max) PSIG: 250
Exhaust Steam Press. PSIG: 40
Rated Power HP: 140
Speed RPM: 4000
Turbine shall be:
Manufactured According To API (611), Last edition.
In-between bearing design, horizontally split casing with centerline support (upper half can be removed without disconnecting inlet & exhaust piping).
Back pressure design.
Equipped with sleeve type radial bearing, ring lubricated, water cooled with water specification (3.5 bar 32 °c) and antifriction thrust ball bearing.
Equipped with floating carbon seal rings on both sides.
Turbine shall be furnished with:
TG 13 Governor.
Thermometer for both bearing housings.
Strainer at turbine inlet.
Adequate cooler, if necessary.
- Pumps are accepted, exclusively, from the following origins: (USA West European Japan).
- Turbine manufacturer should be one of the following: (Elliott / Peter-Brotherhood).
|Bid Bond||1% of submitted prices|
|Documents Price||ID 150,000|